Build over infrastructure
Building work over or near sewers, water mains, stormwater drains and combined sanitary drains must be assessed against the Queensland Development Code MP 1.4 – Building over or near relevant infrastructure (PDF, 515KB).
MP 1.4 provides consistent and tailored standards across Queensland. A range of default building solutions are available to property owners.
Where MP 1.4 applies
MP 1.4 applies to:
- building work to be carried out for a building or structure on a lot that contains, or is adjacent to, relevant infrastructure
- lots where an adjacent road reserve contains relevant infrastructure
- land that is the subject of an easement registered by a relevant service provider through the Titles Registry.
Where MP 1.4 doesn't apply
MP 1.4 doesn't apply to:
- building work that is further than a specified minimum distance from the infrastructure, including:
- sufficiently clear from the zone of influence
- 3 metres away for a Class 1 or 10 building or structure
- 5 metres away for a Class 2–9 building
- 5 metres away for driven piles or piers
- 10 metres away for ground anchors or rock bolts
- internal alterations or repairs to existing buildings or structures that don't:
- increase the floor area
- affect the footing system or sub-structure
- self-assessable building work for a structure (e.g. a fence or retaining wall), unless the structure is supported by a strip footing. See Schedule 1 of the Building Regulation 2006 for self-assessable types of building work.
If MP 1.4 doesn't apply, the building development application can continue without service provider or local government consent, because adequate protection will be provided without further assessment or conditions.
Local governments and service providers are referral agencies in the application approval process.
Under the Planning Regulation 2017, a 'relevant service provider' is a referral agency for building work regulated under MP 1.4.
Relevant service providers are sewerage service providers and water service providers that are both:
- registered under the Water Supply (Safety and Reliability) Act 2008
- the owner of a stormwater drain.
An application must be referred to a referral agency if the work either:
- doesn't comply with an acceptable solution for the MP 1.4 performance criteria
- is for a Class 2–9 building that is less than 5 metres from the relevant infrastructure.
Referral agencies have 20 business days to assess the application. They may charge a fee.
Combined sanitary drains
Applications involving combined sanitary drains don't need a referral agency because they’re usually:
- shared by more than one lot owner
- not owned by a service provider.
In these cases, the assessment manager assesses an alternative solution.
Keeping service providers informed
Service providers must be informed about any building work located near their infrastructure to help them in their inspections, maintenance and repair duties.
Building certifiers must provide a Form 32—Relevant information for service providers (PDF, 62KB) to sewerage service providers in specific cases.
Read more in our information for private building certifiers (PDF, 71KB).
A person may appeal a decision relating to MP 1.4 to the Development Tribunals, including a decision to impose conditions, grant a refusal or approve a building development.
- Last reviewed: 6 Aug 2020
- Last updated: 26 Nov 2019